我国还没有具体的洗眼器法律法规，目前主要有两个标准参考，1、美标 ANSI Z358.1-2004，2，欧标 DIN-12899,但是，我国大多数执行的还是美标。
ANSI Z358-1 2004 :
The following specifications are taken directly from the ANSI Z358.1-2004standard.
SHOWERS (Plumbed and Self-Contained)
Plumbed Shower: An emergency shower permanently connected to a source of potable water. Self-Contained Shower: A shower that contains its own flushing fluid, and must be refilled or replaced after use.
The specifications below are for plumbed showers only.
A. Positioned no less than 82 from floor.
B. Spray pattern will have a minimum diameter of 20 at 60 above the floor.
C. Flow Rate=20 gallons per minute (GPM) at a velocity low enough to be non-injurious to the user.
D. Center of spray pattern shall be located at least 16 from any obstruction.
A. Off to On in 1 second or less.
B. Stay-open valve (no use of hands).
C. Valve remains on until the user shuts it off.
A. 10 seconds from the hazard. Must be on same level as the hazard and the path of travel shall be free of obstructions that inhibit the immediate use of the equipment.
B. Shower location shall be in a well-lit area and identified with a sign.